What people are saying - Write a review
We haven't found any reviews in the usual places.
Other editions - View all
air supply ANSI approved ASTM automatic boiler Btus building code building official building or structure chamber Chlorodifluoromethane Chloropentafluoroethane clearance combustible material connected connector constructed cooling degrees F diameter discharge draft hood eighteen 18 evaporative cooling exhaust system fireresistance rated floor flue fuel furnace fusible plug Gage gas-fired gases heaters heating equipment heating system hot water hundred 100 inches incinerator inlet inspection agency installed in accordance iron pipe size jurisdiction least less liquid listed in Appendix located machinery room main burner Masonry chimneys mechanical ventilating Metal chimneys minimum nationally recognized testing NFiPA noncombustible occupancies one-half openings operating outlet permit plenums pressure vessel pressure-relief device products of combustion range hoods refractory refrigerant refrigerating system roof Section shut-off valve side space specifications Standard standpipe steam steel storage sulfur dioxide tank temperature testing or inspection tubing twelve 12 unit vapors vent vertical wall warm air weld
Page 20 - ... or is not sufficiently supported, ventilated, sewered, drained, cleaned or lighted, in reference to its intended or actual use; and whatever renders the air or human food or drink unwholesome, are also severally, in contemplation of this act, nuisances; and all such nuisances are hereby declared illegal. (19) Construction of Certain Words. The word "shall...
Page 8 - ... the distributing pipes of a potable supply of water from any source or sources other than its intended source.
Page 4 - The provisions of this code are not intended to prevent the use of any material or method of construction not specifically prescribed by this code, provided any such alternate has been approved.
Page 114 - Listed flexible metal hose may be used to reduce the effect of jarring and vibration or where rigid connections are impracticable and shall be installed in full compliance with its listing.
Page 4 - ... of this code and that the material, method or work offered is, for the purpose intended, at least the equivalent of that prescribed in this code in suitability, strength, effectiveness, fire resistance, durability, safety and sanitation.
Page 159 - Manually operated dampers shall not be placed in chimneys, vents or connectors of stoker fired, liquid or gas-burning appliances. Fixed baffles on the appliance side of draft hoods and draft regulators shall not be classified as dampers.
Page 3 - ... officer or official board of the jurisdiction may apply to the appropriate court for a writ of certiorari to correct errors of law in such decisions.
Page 163 - Room is a room in which a refrigerating system is permanently installed and operated but not including evaporators located in a cold storage room, refrigerator box, air cooled space, or other enclosed space. Closets solely contained within, and opening only Into, a room shall not be considered machinery rooms, but shall be considered a part of the machinery room in which they are contained or open into. It is not the intent of this definition to cause the space in which a self-contained system is...
Page 248 - Any party may move the court to remit the case to the commission in the interests of justice for the purpose of adducing additional specified and material evidence and seeking findings thereon, provided he shows reasonable grounds for the failure to adduce such evidence before the commission.